- Application Instructions
- Order References / Sizes
- Shipping & Returns
Where conduits pass through fire-rated ceilings and walls, it is a requirement to terminate each side with a BESA or universal box fitted with intumescent gaskets to stop fire penetrating. It is also a requirement to fit intumescent gaskets in the back of metal switch/socket boxes where they are back-to-back and cables pass through the wall. Our extensive range of expanding intumescent gaskets and linings can be used with a wide range of standard electrical boxes.
– Solutions for both plastic and metal boxes, providing up to 4 hours protection- Compatible with single or double socket or switch boxes, BESA boxes, universal conduit boxes and ceiling roses
– Complies with IEE Wiring Regulations, bringing standard boxes in line with Document B
Intumescent gaskets are essential in metal or plastic boxes where
cables pass back through a wall. Gaskets must be fitted to all dry lining boxes in
partition walls. Without these gaskets fire can spread into the partition within 4-5
minutes. Where cables run through back to back boxes in brick or block walls, flames
can pass through within 6 minutes, resulting in a wall or partition only 6 minutes of
Gaskets for use inside metal or plastic boxes are made to the size of the box and
come with self-adhesive fixing on the back. Once the backing paper has been peeled
off the fixing strip, the gasket can be adhered to the inside of the box. Holes can be
cut into the gasket with a sharp knife to receive cables, or the gasket can be cut to fit
the back of the box if cables are already fitted. Dry lining boxes in walls have two
pads per box, made to size and adhered top and bottom.
Plasterboard ceiling rose boxes can be protected by means of an intumescent cover
which folds up and is passed through the hole in the ceiling. A hole is then cut in the
cover to receive the cables, which are then pulled through the cover, box and ceiling
before connecting the ceiling rose.
Ceiling rose gaskets to fit over the ceiling rose or hook plate should be fitted where
more than two cables pass through the ceiling. A hole is made in the gasket through
which the cables are passed. The backing paper of the self adhesive fixing strip is
then peeled off and the gasket is adhered to the ceiling. The pendant or light fitting
can then be fitted.
REF HEIGHT WIDTH THICKNESS
MMG/132/132 132mm 132mm 3mm
MMG/177/177 177.5mm 177.5mm 3mm
MMG/203/101 203mm 101mm 3mm
MMG/230/230 230mm 230mm 3mm
MMG/241/241 241mm 241mm 3mm
MMG/251/191 251mm 251mm 3mm
MMG/350/290 350mm 290mm 3mm
All of our 'in stock' product orders will be shipped same day, as long as the order has been processed before 3pm - this is simply to be in a position to catch the courier pickups.
Some of couriers are explicit in their non-liquid deliveries so if you have ordered a mixture of ambient and liquid products your order has to be split across two couriers. These are lead by courier company policies, however the courier selection was done of price and so you can be safe in the knowledge that you will be getting the most competitive delivery prices around.
We deliver across the Island of Ireland and aim for 48/72hrs deliveries on all our orders. If you order a product that is 'out of stock' we will get them shipped by our supplier, Envirograf UK over night for our next days deliveries.